Client Daniel T.
Timeframe Same Day
Location Escondido, CA
A home owner called ASAP Drain Guys & Plumbing because their drains were draining slowly and they requested a video inspection to see the condition of their pipes.
The video inspection showed that the sewer line was dirty with minor root intrusions. The sewer line had no clean out and ASAP recommended having a clean out installed.
To repair the toilet, the ASAP technician needed to pull the toilet and cable snake through the closet bend. He ran the 1/2″ cable with double blades 70 feet through the master bath toilet flange to clear the line. He replaced the fill valve on the toilet and snaked the sink in the master bath as well.
ASAP also recommended that the customer replace both toilets in order to remedy the slow flushing issues. The customer would like to provide the toilets and will call ASAP back to have them installed.