A property management company called ASAP Drain Guys & Plumbing because their recirculation pump was making noise and possibly the 2″ pressure regulator needed to be replaced.
The ASAP technician installed one new 2″ single union pressure reducing valve on the water main line outside of the boiler room. The tech tested for leaks and for proper function. There are no leaks at this time and the pressure reducing valve is working properly at this time.
The tech also installed one new flange kit and one new 1/2″ Grunfos flange recirculating pump on the recirculating line in the boiler room. The power line was reconnected to the new pump and tested for proper function and leaks. There are no leaks and everything is working properly at this time. Lastly, the tech cleaned up the work area.