A homeowner called ASAP Drain Guys & Plumbing to do a maintenance check of their home. They have two water heaters that have never been flushed out, several leaking hose bibs, shut off valves that were frozen, and water pressure that needed to be checked. The customer wanted to supply all parts.
The ASAP technician turned off the water heater in the garage. He installed a new sediment trap. He also replaced the gas line because it was short. ASAP supplied the gas line.
The technician replaced the hose bib outside of the garage under the shower valve. He replaced the hose bib near the water heater room. The tech also replaced the shower head in the master bathroom.
More parts needed to be ordered so the technician would come back to this home at a later date.