Client Expert Property Management - Georgia Regency
Timeframe 1 Day
Location San Diego, CA
ASAP Drain Guys and Plumbing was called on a Saturday evening for reports of no hot water to units on the left side of an apartment complex. ASAP technician began by inspecting several units at the apartment complex to ensure only the left side of the building was effected as well as the shut off valves and commercial water heater system. The technician proceeded to to isolate each water heater to determine which water heater belonged to each side of the complex. The water lines where shut off to the corresponding water heater and recirculating pump was unplugged. ASAP installed two new 3/4″ spring check valves to the recirculation line for the water heater as well as new hosebib and shut off valve. Water to water heater was restored and recirculating pump was plugged back into outlet. ASAP inspected for leaks, no leaks were present, then went to check units for hot water. Hot water had been restored back to the left side of the apartment complex.