Client Rancho Carlsbad
Timeframe Same Day
Location Carlsbad, CA
A property management company contacted ASAP Drain Guys & Plumbing during after hours because of a backed up main line.
The ASAP technician found that four units were backed up. He attempted to clear the line through the clean out from unit 5144 but was unsuccessful. He then attempted to clear the blockage through unit 5314 and was able to clear a small hole through root intrusion using a cable snake with blades. He then cleared three different root intrusions that were growing through the clay joints.
The technician video inspected the main line to ensure the root intrusion was clear. The video showed that there was major root intrusion approximately 34 feet downstream. The technician recommended to the management company that the main line be epoxy lined and hydrojetted every 6 months to ensure the lines remain clear.