Client San Diego RV Resort
Timeframe Same Day
Location La Mesa, CA
An RV resort contacted ASAP Drain Guys & Plumbing because their main line was backed up and needed to be inspected and cleared.
The ASAP technician snaked the main line through the proper access clean-out using 11/16” cable. He ran the cable out approximately 75’ before clearing line but pulled nothing back. Next the technician performed video inspection.
The inspection was performed through the cleanout behind space 123. He ran the camera and located several areas of small root intrusions within approximately the first 20’. He also discovered a large obstruction in the pipe at approximately 53’ out. The obstruction looks like it is either a large root crushing the pipe or some concrete that broke through. He located that obstruction and marked it with a blue x. It is located approximately 2.5’ deep. The line has several bellies of water that make it difficult to discern much about other areas of the pipe. ASAP ran the camera out a total of 90’ and located the property drop portion of the pipe.