On 8-13-20 ASAP was called out for an Armstrong boiler pump leaking and hissing. ASAP technician removed existing broken Armstrong boiler pump and installed one new Taco 0012 boiler pump and volute. Technician also installed new conduit between boiler pump and boiler.
Tested by turning on boiler system. Tested good. Completed cleanup of work area.