Client Allegis SHE Property Management
Timeframe Same Day
Location San Diego, CA
ASAP Drain Guys & Plumbing performed annual maintenance on two Raypak boilers for a multifamily property in San Diego, CA.
ASAP inspected all visible water lines for the boilers and storage tanks. They inspected and test the boilers, circulation pumps, thermostats, flow switches, valves and ball valves, T&P valves and storage tanks, and expansion tanks. The tech cleaned and inspected the burner assemble and coil pack. The exhaust vent was inspected. Anode rods in the storage tank were replaced. The boiler system was tested for proper functioning.
The tech noticed that boiler #1 gauge was defective and recommended being replaced. There was also corrosion on the brass nipple near the gauge on both boilers. The tech recommended to remove the nipple, clean the threads, and reinstall the nipple for both boilers.