Client Sunrise Management
Timeframe 2 Days
ASAP Drain Guys and Plumbing was called out to inspect a 100 gallon water heater at an apartment complex in Vista, CA. Once the tech was on site he found that there was a leak coming from the bottom of the tank. He proposed to replace the tank with a similar unit. After receiving approval to replace the water heater, ASAP began by turning off the gas and water to the heater and proceeded to disassemble all of the connections to the heater. A new 100 gallon water heater was then installed along with new expansion tank.
After the installation of the 100 gallon water heater was installed, ASAP technician tested the unit and connections for any leaks and for proper function.